Battery connections made with tab washers on a four-cell jar. The bank must be taken offline to make this type of connection.
Stationary battery systems are among the most critical substation assets and are often the most overlooked. Recent changes to the North American Electric Reliability Corporation’s (NERC’s) Protection System Maintenance requirements, PRC-005-2 in particular, have placed new importance on these critical systems by including strict inspection, testing and maintenance requirements for bulk electric system (BES) battery systems. This document makes clear distinction between ...
Website Registration Required to Access this Content
Only registered users have access to Silver content.
Registration on tdworld.com allows you exclusive access to high-value content such as Transmission & Distribution World supplements: Smart Grid, Renewables, Vegetation Management, Linemen, and Hurricane Sandy.